#117 | NPower and Tape Drive Power Supply
|Product||Liebert NX Series UPS|
|Application||Military / Datacenter|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass, Inverter operating, unit unable to transfer online.|
|Preliminary Actions||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass|
|Resolution||Replaced blown output fuse along with other output fuses, tested UPS, placed system back online.|
|Root Cause||One of the tape drives in the data center had a faulty / shorted power supply which was detected on the output of the UPS, enough so that it cleared an Output fuse on the UPS.|
The UPS protected itself by clearing the fuse prior to allowing further damage to the Inverter. Note that periodic inspections should also be considered for the end user’s data center servers / tape drive equipment to insure proper operation within specifications.
Images Credit: Images courtesy of IBM®
News Article More and more critical power customers, whether their critical power assets are managed by a representative of their IT department, Facilities or even Procurement, are opting to adopt the “we’ll fix it when it breaks” mentality. The cost to maintain their...
News Article The fastest growing waste streams in the industrialized world are discarded electronics equipment due to the growing use of these products. In the UPS industry, companies do their part to help reduce the carbon footprint and support a cleaner, more...
News Article UPS Systems are complex pieces of highly technical electronic equipment and need regular preventive maintenance (PM). The maintenance intervals can vary from one to four PM inspections per year or in some cases, even monthly. The top main causes for UPS...