Case Study #106 | Thermal Runaway
|Application||Medical Facility Data Center|
|Synopsis||Some maintenance-free, rechargeable sealed Valve Regulated Lead Acid (VRLA) UPS batteries can experience Thermal Runaway conditions. Higher ambient temperatures, high charge/re-charge current, age, overuse, shorted (bad) internal cells, loose connections and poor design can be factors. Thermal condition of a battery is also dependent on its environment. If the battery’s temperature is higher than the ambient temperature, it will normally lose heat through conduction, convection and radiation. However, if the ambient temperature is higher, the battery will gain heat from its surroundings causing the thermal management system to work harder to keep the resulting heat under control. A single cell may work very well at room temperature on its own, but when it is surrounded by other batteries or modules generating heat, this will cause the temperature to rise, which will lead to thermal runaway and possible a very destructive situation:|
|Resolution||Replace the batteries and have regular preventive maintenance performed by a reputable UPS maintenance company.|
|Root Cause||This was an older UPS that did not have regular preventive maintenance performed. Proper cooling, airflow, and maintenance will reduce exposure of thermal runaway conditions.|
Case Study In this Nationwide Power™ case study, we hope to show our customers another example of how a full-service contract will save our customers time, money, and headaches in both the short term and in the long run. In this case study, we particularly focus in...
News Article As the year 2020 has come to a close, we’re all looking forward to a better and brighter year ahead in 2021. For a lot of companies throughout the country, business came to a pause in late March of last year. Nationwide Power™ was no exception. However,...
News Article We’re excited to share that our partners at Eaton have released the new Ferrups FX UPS! Below is an excerpt from Eaton. Click here to learn more. “Combining a reliable and customizable design with a remote-control display screen featuring a LED bar, the...