Case Study #106 | Thermal Runaway
|Application||Medical Facility Data Center|
|Synopsis||Some maintenance-free, rechargeable sealed Valve Regulated Lead Acid (VRLA) UPS batteries can experience Thermal Runaway conditions. Higher ambient temperatures, high charge/re-charge current, age, overuse, shorted (bad) internal cells, loose connections and poor design can be factors. Thermal condition of a battery is also dependent on its environment. If the battery’s temperature is higher than the ambient temperature, it will normally lose heat through conduction, convection and radiation. However, if the ambient temperature is higher, the battery will gain heat from its surroundings causing the thermal management system to work harder to keep the resulting heat under control. A single cell may work very well at room temperature on its own, but when it is surrounded by other batteries or modules generating heat, this will cause the temperature to rise, which will lead to thermal runaway and possible a very destructive situation:|
|Resolution||Replace the batteries and have regular preventive maintenance performed by a reputable UPS maintenance company.|
|Root Cause||This was an older UPS that did not have regular preventive maintenance performed. Proper cooling, airflow, and maintenance will reduce exposure of thermal runaway conditions.|
News Article It is with great pride to announce that our team at Nationwide Power celebrates our 18th year in business! Over the years, we have grown to have the largest national footprint among UPS service providers, and we have built our business on one key...
News Article It was recently announced that certain EnerSys and Exide GNB UPS battery models have been discontinued and product availability is quickly depleting or no longer exists. The following UPS batteries are included in this list:Discontinued...
In this Nationwide Power Case Study, we are highlighting a technical support call for a 16kVA APC Symmetra LX RM UPS for bad battery modules.