Case Study #106 | Thermal Runaway
|Application||Medical Facility Data Center|
|Synopsis||Some maintenance-free, rechargeable sealed Valve Regulated Lead Acid (VRLA) UPS batteries can experience Thermal Runaway conditions. Higher ambient temperatures, high charge/re-charge current, age, overuse, shorted (bad) internal cells, loose connections and poor design can be factors. Thermal condition of a battery is also dependent on its environment. If the battery’s temperature is higher than the ambient temperature, it will normally lose heat through conduction, convection and radiation. However, if the ambient temperature is higher, the battery will gain heat from its surroundings causing the thermal management system to work harder to keep the resulting heat under control. A single cell may work very well at room temperature on its own, but when it is surrounded by other batteries or modules generating heat, this will cause the temperature to rise, which will lead to thermal runaway and possible a very destructive situation:|
|Resolution||Replace the batteries and have regular preventive maintenance performed by a reputable UPS maintenance company.|
|Root Cause||This was an older UPS that did not have regular preventive maintenance performed. Proper cooling, airflow, and maintenance will reduce exposure of thermal runaway conditions.|
News Article Band-Aid fixes don’t actually fix problems – we all know that, right? Take a close look at the image above. Do you see what we see? This customer is using a fan to regulate the temperature of the battery cabinet in this Liebert Npower 50kVA UPS. Why?...
News Article At Nationwide Power, we take training and continuing education very seriously. In fact, we consider our rigorous curriculum to be one of the key components that sets Nationwide Power apart from the sea of alternative UPS service providers in the market....
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...