Case Study #106 | Thermal Runaway
|Application||Medical Facility Data Center|
|Synopsis||Some maintenance-free, rechargeable sealed Valve Regulated Lead Acid (VRLA) UPS batteries can experience Thermal Runaway conditions. Higher ambient temperatures, high charge/re-charge current, age, overuse, shorted (bad) internal cells, loose connections and poor design can be factors. Thermal condition of a battery is also dependent on its environment. If the battery’s temperature is higher than the ambient temperature, it will normally lose heat through conduction, convection and radiation. However, if the ambient temperature is higher, the battery will gain heat from its surroundings causing the thermal management system to work harder to keep the resulting heat under control. A single cell may work very well at room temperature on its own, but when it is surrounded by other batteries or modules generating heat, this will cause the temperature to rise, which will lead to thermal runaway and possible a very destructive situation:|
|Resolution||Replace the batteries and have regular preventive maintenance performed by a reputable UPS maintenance company.|
|Root Cause||This was an older UPS that did not have regular preventive maintenance performed. Proper cooling, airflow, and maintenance will reduce exposure of thermal runaway conditions.|
Case StudyIn this Nationwide Power™ (NP™) case study, we show the importance of regularly scheduled maintenance inspections and replacements of age-based components. This case study focuses specifically on the replacement of batteries on a Best FerrUPS FE18kVA. An...
News Article Corks popping and fireworks fireworkin’. That’s the sound of our team celebrating! Each year, approximately 1,500 companies are invited to compete for a spot on the “Top Workplaces” list . The process is extensive and relies on anonymous surveys and...
Case StudyNationwide Power™ (NP™) is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries. Our 57,000 square foot warehouse, with over $10 million in parts and...