Case Study #108 | “Maintenance-Free” Batteries
|Product||“Maintenance-Free” VRLA Batteries|
|Application||Business Electrical Room|
|Synopsis||Customer had called for a trouble-shoot and possible shut-down of the UPS|
|Preliminary Actions||The Nationwide Power engineer was on-site to trouble-shoot a UPS unit that was in alarm, and to remove leaking/cracked batteries.|
|Resolution||The UPS was being used to power emergency lighting for 3 buildings and had been running in alarm with batteries shorting to ground for a long time. Upon arrival, the engineer found the UPS with an active rectifier alarm and concluded that the UPS needed new AC and DC capacitors, new fans, and a full battery replacement. The DC link would not return to nominal voltage with batteries being disconnected and the logic was showing other rectifier alarms, signifying potential rectifier issues or logic problems. There were also multiple battery contactor alarms active. The UPS was put into internal maintenance bypass with logic turned off until it can be replaced or repaired. The system may need to be completely replaced.|
|Root Cause||“Maintenance-Free” does not mean that the whole Uninterruptible Power Supply does not need to be maintained. To have maintenance-free batteries simply means that you do not have to add water (as with flooded cell batteries). Some might contend that you do not have to re-torque connections either, however most VRLA battery manufacturer maintenance instructions state they should be re-torqued annually. Regular inspections where voltages and ohmic readings are taken would have electrically identified the battery as trending bad prior to the battery visually indicating the swelling, cracking, and leakage.|
News Article Thank you, Stanley Bryan, Critical Power Professional™ at Nationwide Power™, for your daily commitment to quality and service! Each day, our Critical Power Professionals (CPP™) do their part in ensuring our customers receive the highest level of service...
News Article With excitement, we are proud to announce the recent promotion of Ryan Murphy to VP of Sales for Nationwide Power™. Ryan has a long-standing history with Nationwide Power, dating back to 2003, where he led growth efforts in the greater Chicago area....
Case Study Part of the job of our Critical Power Professionals™ (CPP™) is to educate our customers on their Uninterruptible Power Supply (UPS) equipment over the lifespan of their system. In this Nationwide Power ™ case study, we feature a scenario where our CPPs...