Case Study #108 | “Maintenance-Free” Batteries
|Product||“Maintenance-Free” VRLA Batteries|
|Application||Business Electrical Room|
|Synopsis||Customer had called for a trouble-shoot and possible shut-down of the UPS|
|Preliminary Actions||The Nationwide Power engineer was on-site to trouble-shoot a UPS unit that was in alarm, and to remove leaking/cracked batteries.|
|Resolution||The UPS was being used to power emergency lighting for 3 buildings and had been running in alarm with batteries shorting to ground for a long time. Upon arrival, the engineer found the UPS with an active rectifier alarm and concluded that the UPS needed new AC and DC capacitors, new fans, and a full battery replacement. The DC link would not return to nominal voltage with batteries being disconnected and the logic was showing other rectifier alarms, signifying potential rectifier issues or logic problems. There were also multiple battery contactor alarms active. The UPS was put into internal maintenance bypass with logic turned off until it can be replaced or repaired. The system may need to be completely replaced.|
|Root Cause||“Maintenance-Free” does not mean that the whole Uninterruptible Power Supply does not need to be maintained. To have maintenance-free batteries simply means that you do not have to add water (as with flooded cell batteries). Some might contend that you do not have to re-torque connections either, however most VRLA battery manufacturer maintenance instructions state they should be re-torqued annually. Regular inspections where voltages and ohmic readings are taken would have electrically identified the battery as trending bad prior to the battery visually indicating the swelling, cracking, and leakage.|
News Article As we look back on 2019, we have much to celebrate. As our business continues to grow, our focus on quality has never been stronger. Here are a few of our favorite highlights:Celebrating our 18th year in business, in which time we have established...
News Article Last month, we brought our company leaders from across the country together to talk about one very important topic: quality. At Nationwide Power, we take the Phil Crosby approach to defining quality, whereas quality is simply conformance to...
Case Study At Nationwide Power, we talk about quality often. We define quality as conformance to requirements, and the result of a carefully constructed cultural environment. As a direct result of establishing processes and procedures, which are then closely...