Case Study #117 | NPower and Tape Drive Power Supply
|Product||Liebert NX Series UPS|
|Application||Military / Datacenter|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass, Inverter operating, unit unable to transfer online.|
|Preliminary Actions||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass|
|Resolution||Replaced blown output fuse along with other output fuses, tested UPS, placed system back online.|
|Root Cause||One of the tape drives in the data center had a faulty / shorted power supply which was detected on the output of the UPS, enough so that it cleared an Output fuse on the UPS.
The UPS protected itself by clearing the fuse prior to allowing further damage to the Inverter. Note that periodic inspections should also be considered for the end user’s data center servers / tape drive equipment to insure proper operation within specifications.
Images Credit: Images courtesy of IBM®
News Article With hundreds of UPS equipment options on the market, ranging from manufacturer, model, kVA size and more, Nationwide Power names Eaton’s 93PM the most versatile UPS of 2019. “At Nationwide Power, we sell millions of dollars' worth of equipment each year,...
News Article In mid-February, our team at Nationwide Power hosted the 2019 Power Summit. We flew in team members, vendors, and OEM partners from across the country to talk critical power infrastructure. The week-long Power Summit included topics like 2018 performance,...
News Article At Nationwide Power, we pride ourselves on putting safety and quality at the top of our priority list, and it’s with great pride that we can announce another year in the books with zero safety incidents. Congratulations to our quarterly safety drawing...