Case Study #144 | Early Detection on Liebert Npower Faulty Wires
Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies (UPS) and UPS batteries. Our 57,000 square foot warehouse, with over $10 million in parts and equipment inventory, provides us the ability to service nearly all major makes and models of UPS equipment.
In this case study, a customer had regularly scheduled preventive maintenance (PM) with Nationwide Power for their Liebert Npower UPS system. The Critical Power Professional™ (CPP™) proactively identified faulty component parts, which prevented a possible future alarm and critical load loss.
|Product||Liebert Npower UPS|
|Synopsis||A Critical Power Professional™ (CPP™) conducted regularly scheduled preventive maintenance on the customer’s Liebert Npower UPS. During the minor PM, the CPP found the control wire to the static switch B phase control to be burnt and discolored with an abnormal temperature reading.|
The faulty component parts were identified through visual inspection during a routine minor PM, while the unit was still online. The Critical Power Professional found a static switch B phase control wire burnt and bus bar discolored, along with a 141° temperature reading.
Parts were ordered, shipped, and replaced with minimal downtime to the UPS system and to the critical load.
|Resolution||As a result of routine maintenance by a qualified professional, the issue was caught early and resolved before resulting in an alarm and/or potential critical failure and load loss.|
There should be no substitution for routine preventive maintenance on critical power equipment. Monitoring systems, no matter how thorough or expensive, would not have detected this.
If this situation had gone undetected, especially since the faulty wires were associated with the static switch, it could have resulted in complete system failure and resulting load loss.
For a common list of questions to ask when receiving quotes from multiple service providers, visit us at:
Case Study In this Nationwide Power™ case study, we hope to show our customers another example of how a full-service contract will save our customers time, money, and headaches in both the short term and in the long run. In this case study, we particularly focus in...
News Article As the year 2020 has come to a close, we’re all looking forward to a better and brighter year ahead in 2021. For a lot of companies throughout the country, business came to a pause in late March of last year. Nationwide Power™ was no exception. However,...
News Article We’re excited to share that our partners at Eaton have released the new Ferrups FX UPS! Below is an excerpt from Eaton. Click here to learn more. “Combining a reliable and customizable design with a remote-control display screen featuring a LED bar, the...