Case Study #152 | The Importance of the Critical Power Environment
In this Nationwide Power™ Case Study, we show the importance of a controlled environment and how one can never be over-prepared for the unexpected. This case study specifically looks at the Eaton/Powerware 9330-30kVA UPS.
|Product||Eaton/Powerware 9330-30kVA UPS|
|Synopsis||Our Critical Power Professional (CPP™) was onsite for age-based full capacitor and fan replacements. After completing the installation and trying to bring the unit back online, the display had no characters, and the unit would not come back online.|
|Preliminary Actions||After some initial troubleshooting and tracing back from the display, the CPP™ found that a lizard had shorted out the power supply and damaged the display board.|
|Resolution||The CPP™ ordered a replacement power supply and display boards for next-day delivery. After replacing both boards, the CPP™ was able to bring the unit back online. With a full-service contract to stand behind, the customer was able to secure parts and labor for next-day installation.|
|Root Cause||Component failure was caused by an external source, in this case a lizard that was most likely searching for warmth. From time to time, and in different geographic regions, we encounter some unique environmental situations. Some of these can be prevented with strict environment controls, while others can be more challenging. Use best practices to keep your critical electrical equipment safe.|
Nationwide Power provides 24/7/365 technical support to ensure that everything operates and transitions successfully before, during, and after any power outage.Request a quote Call | 800-868-2780 E-Mail
We are your critical power infrastructure partner!
Case Study #156 | Importance of Following Age Based Recommendations
Case StudyIn this Nationwide Power™ (NP™) case study, we highlight the importance of following your service provider’s age-based components. The most common age-based components are batteries (every 3-5 years), fans (every 5 years), capacitors (every 5-7 years), and...
Case Study #155 | Knowing Your Infrastructure
Case StudyIn this Nationwide Power™ (NP™) case study, we highlight the importance of knowing what your electrical infrastructure is, and what is supported by your UPS. This case study specifically looks at the Eaton Powerware 9330-15kVA UPS. Product 9330-15kVA UPS...
Case Study #154 | Check Battery Alarm
Case StudyIn this Nationwide Power™ (NP™) case study, we show the importance of regularly scheduled maintenance inspections and replacements of age-based components. This case study focuses specifically on the replacement of batteries on a Best FerrUPS FE18kVA. An...