Case Study #155 | Knowing Your Infrastructure
In this Nationwide Power™ (NP™) case study, we highlight the importance of knowing what your electrical infrastructure is, and what is supported by your UPS. This case study specifically looks at the Eaton Powerware 9330-15kVA UPS.
|Synopsis||An existing customer placed a service call stating their Eaton 9330 UPS went into bypass and that there was an electrical smell in the room.|
|Preliminary Actions||Initial phone troubleshooting was not able to place the unit back online, so one of our Critical Power Professionals™ (CPPs™) was dispatched to the site.|
Upon arrival, our CPP began troubleshooting and found the unit in maintenance bypass. A visual inspection showed nothing outstanding. After downloading the alarm history, multiple overload alarms were logged with some above 125%.
Further review of the load on the UPS identified laser printers, air purifiers, and shredders plugged into receptacles supported by the UPS. Once these non-essential loads were removed from the UPS, there were no more overload issues.
To avoid a possible return call, the CPP also performed a load test on the batteries while onsite, which all batteries passed.
As for the electrical smell the customer identified, it was not related to the UPS and possibly came from another piece of equipment in the room.
Without knowing what the electrical infrastructure/receptacles supported by the UPS are, as well as connecting non-essential equipment into UPS supported receptacles, a business is opening themselves up to possible downtime and costly repairs.
It is also best practice to track data over time during maintenance inspections to look for any trends. The PM inspection prior to this visit showed normal loads on the UPS.
News Article As the winter season approaches, it's an ideal time to contemplate the maintenance of your Uninterruptible Power Supplies (UPS) and, more specifically, the replacement of UPS batteries. UPS systems are a crucial component of safeguarding your...
News Article Corks are popping, and the excitement is overflowing at Nationwide Power as we celebrate a remarkable achievement. For the second year in a row, our organization has been named a Top Workplace, solidifying our position as a leader in creating a culture of...
Case StudyIn this Nationwide Power™ (NP™) case study, we highlight the importance of following your service provider’s age-based components. The most common age-based components are batteries (every 3-5 years), fans (every 5 years), capacitors (every 5-7 years), and...