#115 | AP600 Fire Panel EPO
|Product||Liebert AP600 Series UPS|
|Synopsis||Customer called in with a report of the UPS being down and tripped off-line. Maintenance Bypass operation had taken place prior to arrival. Possible damage to equipment.|
|Preliminary Actions||Upon arrival, found UPS in Maintenance Bypass Mode. Restart attempts were unsuccessful.|
|Resolution||Replacement components had to be ordered to address possibly damaged components.|
|Root Cause||Customer had the local Fire Department on site performing testing. The Fire Panel is tied to the UPS via shunt trip, and upon testing, the UPS was deactivated. Considering the Maintenance Bypass Panel was in use upon arrival, suspect this was operated in order to try and restore power back to the load, and possible internal UPS damage has occurred.
Recommend customer give consideration to UPS 101 Critical Power customer training in order to better understand system functionality and operation, and also become familiarized with site-specific system functionality as it relates to facility operations.
News Article More and more critical power customers, whether their critical power assets are managed by a representative of their IT department, Facilities or even Procurement, are opting to adopt the “we’ll fix it when it breaks” mentality. The cost to maintain their...
News Article The fastest growing waste streams in the industrialized world are discarded electronics equipment due to the growing use of these products. In the UPS industry, companies do their part to help reduce the carbon footprint and support a cleaner, more...
News Article UPS Systems are complex pieces of highly technical electronic equipment and need regular preventive maintenance (PM). The maintenance intervals can vary from one to four PM inspections per year or in some cases, even monthly. The top main causes for UPS...