#119 | General Housekeeping
|Product||Critical Power / Electrical Equipment|
|Application||Critical Power / Electrical / Switchgear Room|
|Resolution||Recommending to clients the continuous importance of proper housekeeping and electrical room cleanliness in accordance with codes and regulations.|
|Root Cause||There are many instances encountered by field service personnel where the critical power and/or electrical room is also used for ‘storage’ or overflow of miscellaneous company items such as: Janitorial supplies, Copy Room Supplies (paper reams), Record Retention (Financial / Personal data), etc.
These rooms should not be used for storage / overflow because they fall under the guidance of both safety and electrical codes and regulations, such as the NFPA’s code for ‘Clear Spaces’ which states;
Working space required by other codes and standards shall not be used for storage. This space shall be kept clear to permit safe operation and maintenance of electrical equipment.
Companies should heed the recommendations of their electrical and field service providers when it is recommended to remove storage / overflow items form these rooms, to support a safer work environment, and one that meets the proper safety and electrical codes and standards.
News Article More and more critical power customers, whether their critical power assets are managed by a representative of their IT department, Facilities or even Procurement, are opting to adopt the “we’ll fix it when it breaks” mentality. The cost to maintain their...
News Article The fastest growing waste streams in the industrialized world are discarded electronics equipment due to the growing use of these products. In the UPS industry, companies do their part to help reduce the carbon footprint and support a cleaner, more...
News Article UPS Systems are complex pieces of highly technical electronic equipment and need regular preventive maintenance (PM). The maintenance intervals can vary from one to four PM inspections per year or in some cases, even monthly. The top main causes for UPS...