Case Study #114 | Maintenance Bypass Mis-Operation
|Product||APC Silcon 60kVA Maintenance Bypass|
|Synopsis||Customer called in with a report of the UPS being in Bypass. Additionally reported that some circuits had gone out and it tripped the UPS unit to Bypass mode with an Internal Hardware Fault.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode with Internal Error Alarm. Also found all three Maintenance Bypass Breakers, Q1, Q2 and Q3 all closed at the same time.|
|Resolution||Opened Q3 and UPS came on-line in Normal Operation. Reviewed alarm history and overall condition of UPS prior to departing site. UPS on-line with no alarms.|
|Root Cause||Customer had an HVAC failure on site, and in response to the failure, plugged in several spot coolers which created an overload condition on the UPS system. In reaction to the overload, someone accidentally mis-operated the Maintenance Bypass Panel in an effort to restore proper operation to the UPS. The UPS went into ‘protective’ mode. Recommend customer give consideration to UPS 101 Critical Power customer training in order to better understand system functionality and operation.|
Look what our CPP™ found on a not-so-routine UPS-battery-install-for-Mitsubishi-UPS-2033D-30kVA
News Article Commitment. Dedication. Teamwork. Sounds like Nationwide Power and the spirit of the Ironman race have a few things in common. Nationwide Power was proud to sponsor two relay teams participating in the St. George 70.3 Ironman this past weekend, one of...
Case Study “We don’t want to take a chance on our UPS system not working.” “What if there’s an outage while you’re doing your PM?” “Can’t you just do all your checks with the UPS online?” “We’re not ready to take that chance while you inspect it.” All of the above...