Case Study #114 | Maintenance Bypass Mis-Operation
|Product||APC Silcon 60kVA Maintenance Bypass|
|Synopsis||Customer called in with a report of the UPS being in Bypass. Additionally reported that some circuits had gone out and it tripped the UPS unit to Bypass mode with an Internal Hardware Fault.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode with Internal Error Alarm. Also found all three Maintenance Bypass Breakers, Q1, Q2 and Q3 all closed at the same time.|
|Resolution||Opened Q3 and UPS came on-line in Normal Operation. Reviewed alarm history and overall condition of UPS prior to departing site. UPS on-line with no alarms.|
|Root Cause||Customer had an HVAC failure on site, and in response to the failure, plugged in several spot coolers which created an overload condition on the UPS system. In reaction to the overload, someone accidentally mis-operated the Maintenance Bypass Panel in an effort to restore proper operation to the UPS. The UPS went into ‘protective’ mode. Recommend customer give consideration to UPS 101 Critical Power customer training in order to better understand system functionality and operation.|
News Article With hundreds of UPS equipment options on the market, ranging from manufacturer, model, kVA size and more, Nationwide Power names Eaton’s 93PM the most versatile UPS of 2019. “At Nationwide Power, we sell millions of dollars' worth of equipment each year,...
News Article In mid-February, our team at Nationwide Power hosted the 2019 Power Summit. We flew in team members, vendors, and OEM partners from across the country to talk critical power infrastructure. The week-long Power Summit included topics like 2018 performance,...
News Article At Nationwide Power, we pride ourselves on putting safety and quality at the top of our priority list, and it’s with great pride that we can announce another year in the books with zero safety incidents. Congratulations to our quarterly safety drawing...