Case Study #120 | Environmental & Equipment Cooling
|Product||Chloride EPEM Critical Power UPS|
|Synopsis||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass.|
|Preliminary Actions||Visually inspected caps and tested warm batteries. Verified batteries to not to be issue. Adjusted equipment ‘levelers’, moved unit away from wall and removed back panel. Found 3 of the 5 cooling fans not spinning with warm internals. No open fan fuses found.|
|Resolution||Recommending to clients the continuous importance of proper housekeeping and electrical room cleanliness in accordance with codes and regulations, and pro-active replacement of aging cooling fans.|
|Root Cause||Insufficient cooling due to dirty / dusty environment and aging cooling fans within the equipment that needed pro-active replacement prior to the time of failure.|
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...
News Article People. Process. Product. Our team members are a cornerstone of our business. Every now and then, we have an opportunity to celebrate the great work we do together, outside of the office. Last month, our Las Vegas-based corporate office came together with...
News Article As Nationwide Power’s way to say “Thank You!” to our team members for always keeping safety top of mind, four winners are drawn quarterly to receive a mini-shopping spree on us. And the winners for this quarter are… drum roll please… Warehouse &...