Case Study #120 | Environmental & Equipment Cooling
|Product||Chloride EPEM Critical Power UPS|
|Synopsis||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass.|
|Preliminary Actions||Visually inspected caps and tested warm batteries. Verified batteries to not to be issue. Adjusted equipment ‘levelers’, moved unit away from wall and removed back panel. Found 3 of the 5 cooling fans not spinning with warm internals. No open fan fuses found.|
|Resolution||Recommending to clients the continuous importance of proper housekeeping and electrical room cleanliness in accordance with codes and regulations, and pro-active replacement of aging cooling fans.|
|Root Cause||Insufficient cooling due to dirty / dusty environment and aging cooling fans within the equipment that needed pro-active replacement prior to the time of failure.|
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...
News Article The industry of uninterruptible power supply is an interesting one. Over the years, we have seen UPS service providers make claims that become challenging for them to fulfill due to being beyond their current infrastructure.When comparing quotes from...
News Article As a part of our holiday tradition, the corporate team at Nationwide Power came together to celebrate another successful year. Each year, Nationwide Power selects a local business to support, and this year’s location was at the family-owned Italian...