Case Study #120 | Environmental & Equipment Cooling
|Product||Chloride EPEM Critical Power UPS|
|Synopsis||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass.|
|Preliminary Actions||Visually inspected caps and tested warm batteries. Verified batteries to not to be issue. Adjusted equipment ‘levelers’, moved unit away from wall and removed back panel. Found 3 of the 5 cooling fans not spinning with warm internals. No open fan fuses found.|
|Resolution||Recommending to clients the continuous importance of proper housekeeping and electrical room cleanliness in accordance with codes and regulations, and pro-active replacement of aging cooling fans.|
|Root Cause||Insufficient cooling due to dirty / dusty environment and aging cooling fans within the equipment that needed pro-active replacement prior to the time of failure.|
News Article It is with great pride to announce that our team at Nationwide Power celebrates our 18th year in business! Over the years, we have grown to have the largest national footprint among UPS service providers, and we have built our business on one key...
News Article It was recently announced that certain EnerSys and Exide GNB UPS battery models have been discontinued and product availability is quickly depleting or no longer exists. The following UPS batteries are included in this list:Discontinued...
In this Nationwide Power Case Study, we are highlighting a technical support call for a 16kVA APC Symmetra LX RM UPS for bad battery modules.