Case Study #120 | Environmental & Equipment Cooling
|Product||Chloride EPEM Critical Power UPS|
|Synopsis||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass.|
|Preliminary Actions||Visually inspected caps and tested warm batteries. Verified batteries to not to be issue. Adjusted equipment ‘levelers’, moved unit away from wall and removed back panel. Found 3 of the 5 cooling fans not spinning with warm internals. No open fan fuses found.|
|Resolution||Recommending to clients the continuous importance of proper housekeeping and electrical room cleanliness in accordance with codes and regulations, and pro-active replacement of aging cooling fans.|
|Root Cause||Insufficient cooling due to dirty / dusty environment and aging cooling fans within the equipment that needed pro-active replacement prior to the time of failure.|
News Article With hundreds of UPS equipment options on the market, ranging from manufacturer, model, kVA size and more, Nationwide Power names Eaton’s 93PM the most versatile UPS of 2019. “At Nationwide Power, we sell millions of dollars' worth of equipment each year,...
News Article In mid-February, our team at Nationwide Power hosted the 2019 Power Summit. We flew in team members, vendors, and OEM partners from across the country to talk critical power infrastructure. The week-long Power Summit included topics like 2018 performance,...
News Article At Nationwide Power, we pride ourselves on putting safety and quality at the top of our priority list, and it’s with great pride that we can announce another year in the books with zero safety incidents. Congratulations to our quarterly safety drawing...