Case Study #120 | Environmental & Equipment Cooling
|Product||Chloride EPEM Critical Power UPS|
|Synopsis||The client had a power outage, and the load was protected and switched to the generator. However, after the power was restored, the UPS would not come back online from bypass.|
|Preliminary Actions||Visually inspected caps and tested warm batteries. Verified batteries to not to be issue. Adjusted equipment ‘levelers’, moved unit away from wall and removed back panel. Found 3 of the 5 cooling fans not spinning with warm internals. No open fan fuses found.|
|Resolution||Recommending to clients the continuous importance of proper housekeeping and electrical room cleanliness in accordance with codes and regulations, and pro-active replacement of aging cooling fans.|
|Root Cause||Insufficient cooling due to dirty / dusty environment and aging cooling fans within the equipment that needed pro-active replacement prior to the time of failure.|
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries. Our 57,000 square foot warehouse, with over $10 million in parts and...
Nationwide Power continues to serve businesses across the United States with their critical power needs
News Article Nationwide Power is an essential business, and as such, has continued to service customers across the United States during the COVID-19 pandemic with certain precautions in place. As with many businesses, Nationwide Power saw a decline in demand during...
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...