Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
News Article As the year 2020 has come to a close, we’re all looking forward to a better and brighter year ahead in 2021. For a lot of companies throughout the country, business came to a pause in late March of last year. Nationwide Power™ was no exception. However,...
News Article We’re excited to share that our partners at Eaton have released the new Ferrups FX UPS! Below is an excerpt from Eaton. Click here to learn more. “Combining a reliable and customizable design with a remote-control display screen featuring a LED bar, the...
News Article Thank you, Stanley Bryan, Critical Power Professional™ at Nationwide Power™, for your daily commitment to quality and service! Each day, our Critical Power Professionals (CPP™) do their part in ensuring our customers receive the highest level of service...