Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
Case Study Part of the job of our Critical Power Professionals™ (CPP™) is to educate our customers on their Uninterruptible Power Supply (UPS) equipment over the lifespan of their system. In this Nationwide Power ™ case study, we feature a scenario where our CPPs...
Case Study At Nationwide Power, we make it a top priority to educate our customers on their critical power equipment and keep them informed of any maintenance items on the horizon. In this case study, a customer had regularly scheduled preventive maintenance (PM) for...
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies (UPS) and UPS batteries. Our 57,000 square foot warehouse, with over $10 million in parts and...