Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
Case Study In this Nationwide Power™ case study, we show the importance of having a qualified Critical Power Professional™ (CPP™) perform maintenance on your critical infrastructure equipment. This case study specifically looks at the Liebert NX 120kVA UPS. A...
Case Study In this Nationwide Power™ Case Study, we show the importance of routine maintenance and its impact on the overall health and life of UPS systems. This case study specifically looks at the Toshiba 1600EP 22kVA UPS. A new customer reached out to our team...
Case Study In this Nationwide Power™ case study, we hope to show our customers another example of how a full-service contract will save our customers time, money, and headaches in both the short term and in the long run. In this case study, we particularly focus in...