Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
News Article Band-Aid fixes don’t actually fix problems – we all know that, right? Take a close look at the image above. Do you see what we see? This customer is using a fan to regulate the temperature of the battery cabinet in this Liebert Npower 50kVA UPS. Why?...
News Article At Nationwide Power, we take training and continuing education very seriously. In fact, we consider our rigorous curriculum to be one of the key components that sets Nationwide Power apart from the sea of alternative UPS service providers in the market....
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...