Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
News Article Corks are popping, and the excitement is overflowing at Nationwide Power as we celebrate a remarkable achievement. For the second year in a row, our organization has been named a Top Workplace, solidifying our position as a leader in creating a culture of...
Case StudyIn this Nationwide Power™ (NP™) case study, we highlight the importance of following your service provider’s age-based components. The most common age-based components are batteries (every 3-5 years), fans (every 5 years), capacitors (every 5-7 years), and...
Case StudyIn this Nationwide Power™ (NP™) case study, we highlight the importance of knowing what your electrical infrastructure is, and what is supported by your UPS. This case study specifically looks at the Eaton Powerware 9330-15kVA UPS. Product 9330-15kVA UPS...