Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...
News Article At Nationwide Power, we acquire thousands of new clients annually of all sizes, industries, and scopes of work. Without fail, when new customers come to us for the first time, it’s for a very short list of reasons: Their unit(s) have been out of warranty...
News Article In the spirit of National Recycling Day, Nationwide Power is ready to chime in on the lithium-ion vs sealed lead-acid battery debate. New technology is often a great thing, leading to cleaner, safer, more cost effective, and more efficient ways of...