Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
News Article As we look back on 2019, we have much to celebrate. As our business continues to grow, our focus on quality has never been stronger. Here are a few of our favorite highlights:Celebrating our 18th year in business, in which time we have established...
News Article Last month, we brought our company leaders from across the country together to talk about one very important topic: quality. At Nationwide Power, we take the Phil Crosby approach to defining quality, whereas quality is simply conformance to...
Case Study At Nationwide Power, we talk about quality often. We define quality as conformance to requirements, and the result of a carefully constructed cultural environment. As a direct result of establishing processes and procedures, which are then closely...