Case Study #118 | Symmetra PX Good and Bad Batteries
|Product||APC Symmetra PX|
|Synopsis||Client found the alarms / condition of unit as: UPS in bypass.|
|Preliminary Actions||Upon arrival, found UPS in Bypass Mode.|
|Resolution||Recommending replacement of all batteries in order to provide proper ride-through on battery during transfer from Utility to Generator power.|
|Root Cause||The mixing and matching of old batteries with new batteries, leaving weak batteries within the system, degrading both the system’s ability for proper transfer from one source to another, and the performance of the newer batteries.
Varying resistance values between ‘good’ batteries and ‘bad’ batteries are detrimental to the overall performance of the UPS’ battery strings(s). Due to this inherent charging and discharging change in characteristics, as batteries near their end of life (typically 4-5 years for an average VRLA battery), it is always preferred to replace batteries by entire strings at a time as opposed to as they fail one at a time.
More so, if only replacing batteries as they fail, more often than not this will not be made apparent until the batteries are called upon…resulting in possible loss of load during needed transfers and/or outage support.
News Article As a part of our holiday tradition, the corporate team at Nationwide Power came together to celebrate another successful year. Each year, Nationwide Power selects a local business to support, and this year’s location was at the family-owned Italian...
News Article Nothing says fall like a company chili-cookoff! Chili, cornbread, pellet smoked bacon-wrapped dogs, and all the right toppings. We were really hoping to see the Wienermobile show up… maybe next year. The judges had a pretty challenging task ahead of...
News Article Lead-acid and lithium batteries have many uses in all parts of the world. Lead-acid or lithium batteries are the backbone to any uninterruptible power supply system, and a lot goes into their proper recycling and disposal. The combination of sulfuric acid...