Case Study #123 | Crisis averted: UPS battery install Mitsubishi UPS 2033D 30kVA
|Product||Mitsubishi UPS 2033D 30kVA|
|Application||Manufacturing Data Center|
|Synopsis||New client hired Nationwide Power to inspect and maintain their Mitsubishi UPS 2033D-30kVA, which provides critical power for an existing data center.|
|Preliminary Actions||Upon inspection, our Critical Power Professional (CPP™) found a battery cable inside the battery cabinet, where the cable’s lug eyelet had melted due to improper torquing /fastening to the battery insert by the previous service company.
If left in its current condition, the cable could have melted during an outage causing a domino-effect including breaking the string’s integrity, dumping the load, and possible risk of fire. It could have also caused a ground fault which would have not only dumped the load, but also damaged the UPS.
|Resolution||Our CPP™ team is equipped with some basic universal repair parts, and in this case a spare battery cable saved the day and was promptly replaced. By being prepared, our CPP™ left the battery string in a condition that no longer presented a safety threat and left the UPS in proper working condition.
Ongoing and regular UPS battery inspections are recommended by a qualified Critical Power Professional™.
|Root Cause||The damaged battery cable appears to be the result of negligence from the previous service provider. This should have been identified and repaired in previous inspections and is a basic element of any quality maintenance inspection.|
|Additional Reading||UPS Battery Preventive Maintenance and Service|
News Article Earlier this month, Nationwide Power hosted the 2020 Power Summit, flying in team members, vendors, OEM partners, and guest speakers from across the country to talk critical power and our quality culture. The week-long Power Summit included topics...
Case Study Nationwide Power™ is the leading provider in the critical power supply industry. Our core business is the sales and service of uninterruptible power supplies and UPS batteries, along with supporting other critical power components such as emergency...
News Article Congratulations to the team at Nationwide Power for another consecutive year of zero safety incidents! The team at Nationwide Power is committed to delivering the highest quality standards, and with that comes a strong focus on safety as well. In...