Case Study #123 | Crisis averted: UPS battery install Mitsubishi UPS 2033D 30kVA
|Product||Mitsubishi UPS 2033D 30kVA|
|Application||Manufacturing Data Center|
|Synopsis||New client hired Nationwide Power to inspect and maintain their Mitsubishi UPS 2033D-30kVA, which provides critical power for an existing data center.|
|Preliminary Actions||Upon inspection, our Critical Power Professional (CPP™) found a battery cable inside the battery cabinet, where the cable’s lug eyelet had melted due to improper torquing /fastening to the battery insert by the previous service company.
If left in its current condition, the cable could have melted during an outage causing a domino-effect including breaking the string’s integrity, dumping the load, and possible risk of fire. It could have also caused a ground fault which would have not only dumped the load, but also damaged the UPS.
|Resolution||Our CPP™ team is equipped with some basic universal repair parts, and in this case a spare battery cable saved the day and was promptly replaced. By being prepared, our CPP™ left the battery string in a condition that no longer presented a safety threat and left the UPS in proper working condition.
Ongoing and regular UPS battery inspections are recommended by a qualified Critical Power Professional™.
|Root Cause||The damaged battery cable appears to be the result of negligence from the previous service provider. This should have been identified and repaired in previous inspections and is a basic element of any quality maintenance inspection.|
|Additional Reading||UPS Battery Preventive Maintenance and Service|
News Article With hundreds of UPS equipment options on the market, ranging from manufacturer, model, kVA size and more, Nationwide Power names Eaton’s 93PM the most versatile UPS of 2019. “At Nationwide Power, we sell millions of dollars' worth of equipment each year,...
News Article In mid-February, our team at Nationwide Power hosted the 2019 Power Summit. We flew in team members, vendors, and OEM partners from across the country to talk critical power infrastructure. The week-long Power Summit included topics like 2018 performance,...
News Article At Nationwide Power, we pride ourselves on putting safety and quality at the top of our priority list, and it’s with great pride that we can announce another year in the books with zero safety incidents. Congratulations to our quarterly safety drawing...