Case Study #123 | Crisis averted: UPS battery install Mitsubishi UPS 2033D 30kVA
|Product||Mitsubishi UPS 2033D 30kVA|
|Application||Manufacturing Data Center|
|Synopsis||New client hired Nationwide Power to inspect and maintain their Mitsubishi UPS 2033D-30kVA, which provides critical power for an existing data center.|
|Preliminary Actions||Upon inspection, our Critical Power Professional (CPP™) found a battery cable inside the battery cabinet, where the cable’s lug eyelet had melted due to improper torquing /fastening to the battery insert by the previous service company.
If left in its current condition, the cable could have melted during an outage causing a domino-effect including breaking the string’s integrity, dumping the load, and possible risk of fire. It could have also caused a ground fault which would have not only dumped the load, but also damaged the UPS.
|Resolution||Our CPP™ team is equipped with some basic universal repair parts, and in this case a spare battery cable saved the day and was promptly replaced. By being prepared, our CPP™ left the battery string in a condition that no longer presented a safety threat and left the UPS in proper working condition.
Ongoing and regular UPS battery inspections are recommended by a qualified Critical Power Professional™.
|Root Cause||The damaged battery cable appears to be the result of negligence from the previous service provider. This should have been identified and repaired in previous inspections and is a basic element of any quality maintenance inspection.|
|Additional Reading||UPS Battery Preventive Maintenance and Service|
News Article It is with great pride to announce that our team at Nationwide Power celebrates our 18th year in business! Over the years, we have grown to have the largest national footprint among UPS service providers, and we have built our business on one key...
News Article It was recently announced that certain EnerSys and Exide GNB UPS battery models have been discontinued and product availability is quickly depleting or no longer exists. The following UPS batteries are included in this list:Discontinued...
In this Nationwide Power Case Study, we are highlighting a technical support call for a 16kVA APC Symmetra LX RM UPS for bad battery modules.